Picture 1: What you see above is what you get. Manual is included which is not shown in the photo above. Deadbolt comes with computer remote monitoring signal. When the strike is ready to use, you are able to remotely monitor the "close" or "open" status of your door from your desktop computer (assuming your access controller has networking function and is connected to a network).
Offered here is ONE (1) pieces of BRAND NEW door electric deadbolt / strike with NC (Normally Closed / Fail Safe) function. It also has a monitoring function. This function will send a signal to your access control unit (such as this or ) to inform the unit about the status of the deadbolt, whether it is in "close" or "open" position. Please note that your access control unit must have this monitoring function to be able to utilize this function. Our fingerprint module (click this icon or to buy it) does have this monitoring function.
Face plate: 205L x 35W x 40H (mm)
Strike: 90L x 25W x 2H (mm)
Cover Plate: 215L x 40W x 0.7H (mm)
Bolt: 16mm diameter, stainless steel 16mm throw
Material: Aluminum panel with strongly style and Stainless steel
Voltage: DC 12V
Current: Start 950mA / standby <=100mA (SUPER LOW HEAT!!!)
Patent Designed: Low temperature
Ideal for Wooden / glass / metal / fire proof door
Authority Certification: CE approved
Signal Output: Door status sensor
This item is rated: NC function -- Normally Closed -- Fail Safe (Locked when energized).
Safety function: Built-in voltage spike suppressor
Please note if you need a more advance version that will send monitoring signal to your access control unit as well as the ability to guarantee the bolt will come out / lock at the correct position (via a positioning ball) and not prematurely, then buy this deadbolt
(code:YHBOBSNC / click on this icon) :
Cable connection instruction:
1. Black cable: Connects the black cable to ground of your intelligent power supply.
2. Red cable: Connects the red able to "NC" socket of your intelligent power supply.
3. White cables: connect one of the white cable to ground or "COM" port of your access controller such as or
Connect the other white cable to the signal port of your access controller. In the case of this controller, you connect to "SEN" port ("SEN" means sensor). In the case of this controller, you connect to "MC1" port on JP1 (Jumper 1) .
Hence, when the strike is ready to use, you are able to remotely monitor the "close" or "open" status of your door from your desktop computer (assuming your access controller has networking function and is connected to a network).
ATTENTION 1: Please note that this electric strike can connect directly to access control unit such as listed below, but we do not suggest buyer to do so because it will shorten the lifespan of your access control unit due to high current passing through the electric strike. Instead, you should connect the strike directly to an intelligent uninterruptible power supply (UPS) that has NC/NO output. Make sure your UPS is "intelligent" meaning that it has NC or NO power output and can receive "door open" signal input from your access control.
ATTENTION 2: Normally Opened (NO) or Fail-secure rated electric strike remains locked during loss of power supply. Normally Closed (NC) or Fail-safe rated electric strike requires power to stay locked. When power is lost (such as a blackout), NC or fail-safe Electric Lock Strikes will remain unlocked until power is restored. Electric Strike that is NO rated may not be compliant with your local building / fire safety code. We personally feel that NC rated electric strike is safer. Buyer should check with their local safety code before making decision to buy a NC or NO rated electric strike. In order to ensure that power supply is not intentionally lost (in the event of theft/burglary), we suggest buyer to buy an Uninterruptible Power Supply shown below.